Super easy way to choose the right industrial chiller for your machinery! How to choose the most suitable industrial chiller for your own machinery and equipment. It may be mentioned in the previous article, but many friends may feel a little dizzy when facing a lot of calculation formulas and parameters, so next for everyone This article introduces the selection of a concentrated concentration in the industrial chiller, the essence calculation company in the essence, and it is very simple and easy to understand. It can help everyone to simplify a lot, the specific formula is as follows:
Cooling capacity = chilled water flow × 4.187 × temperature difference × coefficient
Note: (1) The chilled water flow rate refers to the cold water flow rate required for the machine to work, and the unit needs to be converted into liters per second; (2) The temperature difference refers to the temperature difference between the water entering and exiting the machine; 4) When selecting air-cooled chiller, the multiplication factor is 1.3, and when water-cooled chiller is selected, the multiplication factor is 1.1. (5) Select the corresponding machine model based on the calculated cooling capacity.
From the current general habit of calculating how large the chiller is with P, the most important thing is to know the rated cooling capacity. If the general air-cooled 9.07KW looks like, choose a 3P machine. And so on. Therefore, the most important choice of industrial chiller is to find the rated cooling capacity. Therefore, after mastering the calculation formula of the cooling capacity and referring to the notes in the description, we can basically solve how to choose a suitable industrial chiller.
Scan on WeChat